Publication UMA-EN-P – November Table of Contents . User Manual UM to assign an IP address to the MicroLogix. controller. Publication INC-EN-P – October Important . Manual UM .. publication UM, for more information on surge suppression. rm_-en-p – Free ebook download as PDF File .pdf), Text File .txt) or read book online for free. Document Number IN UM
|Published (Last):||28 November 2007|
|PDF File Size:||12.57 Mb|
|ePub File Size:||13.47 Mb|
|Price:||Free* [*Free Regsitration Required]|
Store the equipment in appropriate static-safe packaging when not in use. For more information on proper grounding guidelines, refer to the Industrial Automation Wiring and Grounding Guidelines, publication The Battery Low indicator on the LCD display of the controller shows the status of the replaceable battery. Vertical mounting is not supported due to thermal considerations.
The Belden cable has two signal wires black and clearone drain wire, and a foil shield. Without appropriate precautions, there may be potential difficulties ensuring electromagnetic compatibility in other environments due to conducted as well as radiated disturbance. Wiring Your Analog Channels Analog input circuits can monitor voltage signals and convert them to serial digital data as shown in the following illustration. Combinations of equipment in your system are subject to investigation by the local Uum001 Having Jurisdiction at the time of installation.
Secure the battery connector wires so that it does not block the expansion bus connector as shown below. Place a flat-blade screwdriver in the DIN rail latch at the bottom of the controller.
IN – Rockwell Automation
This could cause an explosion in hazardous location installations. Repeat steps 1 and 2 for the second DIN rail latch. However, because of the variety of applications and environments where analog controllers are installed and operated, it is impossible to ensure that all environmental noise will be removed by the input filters.
You must provide a Customer Support case number call the phone number above to obtain one to your distributor in order to complete the return process. Failure to remove the strip before operating can cause overheating. Output 2, 3 and 4 may be used like the other FET transistor outputs, but in addition, within a limited current range, they may be operated at a higher speed. Use only the following communication cables in Class I, 17766 2 hazardous locations. If you would like a manual, you can: It must be mounted within an enclosure that is suitably designed for those specific environmental conditions that will be present and appropriately designed to prevent personal injury um00 from accessibility to live parts.
Drilled fragments that fall into the controller could cause damage. Throughout this manual, when necessary, we use notes to make you aware of safety considerations. Power Loss in Transmission Lines.
1766-IN001 – Rockwell Automation
Identifies information um010 practices or circumstances that can lead to personal injury or death, property damage, or economic loss. Debris strip ATTENTION Do not remove the protective debris strip until after the controller and all other equipment in the panel near the controller are mounted and wiring is complete. While pressing the controller down against the top of the rail, snap the bottom of the controller into position.
Installation Assistance If you experience a problem within the first 24 hours of installation, please review the information that’s contained in this manual.
Failure to remove strip before operating can cause overheating. All cables connected to the product must remain in the enclosure or be protected by conduit or other means. Remove the mounting template from inside the back cover of this document.
Reproduction of the contents of this manual, in whole or in part, without written permission of Rockwell Automation, Inc. Install your controller using these installation instructions. Specifically, this equipment is intended for use in clean, dry environments Pollution degree 2 1 and with circuits not exceeding Over Voltage Category II 2 IEC 3. Make sure that the placement of the controller on the DIN rail meets the recommended spacing requirements see Controller Spacing on page 12 for more information.
If it is open, close the DIN latch. Because of this difference, and also because of the wide variety of uses for solid state equipment, all persons responsible for applying this equipment must satisfy themselves that each intended application of this equipment is acceptable.